|Filter section||20 micron|
|Material||SS and MS|
|Type||Air Handling Unit|
The Double Skin Air Handling Unit consists of blower section with KRUGER make forward curve DIDW centrifugal high static blowers, SIEMENS / CROMPTON make three phase induction motors, driving accessories, coil section with direct expansion type cooling coil; insulated condensate drain tray, filter section with 20 microns and pre filter mounting frame, mixing box section, return air & 10% F.A. cut outs. The fan assembly mounted on the common base with vibration isolator, flexible canvass connection.
The AHU frame should be the aluminium hollow section with 25mm thick PUF insulation (outer skin CRCA & inner skin G.I.) with enamel finish. Provision of service doors in the blower and mixing box section wherever required and the doors and panels will be sealed with the food grade rubber gasket in order to avoid air leakage.